Because of its advantages, distributed generating (DG) is becoming increasingly popular. It decreases energy loss in the distribution system, lowers voltage fluctuations, improves energy quality, price efficiency, and system dependability. However, integrating these technologies into the national energy system can be difficult. It might cause problems including power system instability, islanding anomalies, and problems altering protective settings.
The procedure of the Energy Storage System (ESS) is as follows:
During off-peak times, when electrical energy is available at lower prices, the ESS system’s procedure can connect with network electrical energy. While this is at the time of charging, the discharging time is when energy in an ESS consumes at its highest.
However, energy storage system (ESS) prices may rise during this period, making using distributed generation (DG) a more cost-effective option.
The most often utilized ESS techniques are determined by the DGs. As a result, ESS may be more closely linked to power electronic equipment that connects to the national power grid.
An Energy Storage System’s interconnection difficulties.
Power systems based on Distributed Generating (DG) can operate both independently and in grid-connected modes. However, in the independent mode, a DG unit’s capacity determines solely by load needs, but in the grid-connected mode, it is not. When it comes to bilateral energy transfers, the grid-connected operation is an option that is frequently considered.
When one or more power plants separate from the national power grid, they serve a portion of the electrical network independently and in response to failures in the main network is the process of islanding. However, the islanding situation is a major concern that you must consider more.
However, operating an ESS in such conditions can result in difficulties such as safety dangers for maintenance and repair personnel, as well as equipment damage owing to voltage and frequency instability.
Problems that might arise when an ESS runs in an Islanding mode:
There may be some technical difficulties:
- The DG’s interconnection to the grid has an impact on the grid’s rotation speed, voltage, and frequency stability. DG can strengthen or worsen the system’s stability depends on the kind and size of the generators.
- Power injected by some DG technologies, such as PV solar power plants, can fluctuate, causing voltage fluctuations.
- Most distributed generators now connect to the grid via electronic circuits, resulting in low-quality power.
- It is difficult to increase the penetration level of DGs. Moreover, it also takes a long time to find any failure in the system, causing the direction of current flow to become unpredictable.
- Power flows in both ways in radial distribution systems that intend to manage power flow in just one direction. The system may then require an upgrade.
- The number of DG units that can link to the system is low. Therefore, to keep the system’s voltage level within the permissible range, the supplied reactive power must be equal to the reactive power demand. This increases the connectedness of the DGs, resulting in higher reactive power provided. As a result, there can be a significant rise in the system’s voltage level.
Read here about the Tesla’s battery dilemma, and how worried should solar installers be about battery fires: https://engineerinc.io/teslas-battery-dilemma-and-how-worried-should-solar-installers-be-about-battery-fires/
There may be economical concerns:
- The network operator must distinguish between electricity from the grid and power from the DGs.
- System enhancements needed can raise the overall cost of the system.
- It is difficult to effectively plan the connectivity of DGs to the grid due to the unpredictability of fuel costs. Therefore, customers may face financial difficulties.